Knowing how to deal with ice in a ductless cooling system is one of the most important tricks to maintain a ductless mini-split unit. You may notice excess condensation in the drain pan, or that ice has accumulated on the evaporator coil. In this case, turn off the unit immediately. Make sure you clear the area around your unit because water may leak out as the ice thaws. To prevent this kind of issue and maintain the efficiency of your mini-split, it’s important to know the common causes.
REASONS ICE FORMS ON DUCTLESS MINI SPLIT UNITS
There are three main causes ice might build up on your evaporator coil. Investigate each of the following to isolate the problem:
Poor Air Circulation
If air isn’t moving over the evaporator coil as it should, it may lead to a buildup. The cold air stays right on top of the coil and freezes the condensation. The air filter may be a problem. If it’s excessively dirty, or otherwise not in working order, it will restrict the airflow. Try cleaning or replacing the filter if it doesn’t appear to be in good condition. The evaporator coil itself may also be defective or dirty. Get regular maintenance on your ductless system to make sure the coil won’t cause you any problems down the road. The last problem is that the fan or blower may be failing to move air away from the coil. Regular inspections should help you keep the peace of mind that your fan is working properly. Also, make sure that nothing around the unit could be blocking the free movement of air.
If your ductless air conditioner freezes up, it may be because the refrigerant is low. The lack of refrigerant will cause the air conditioner to work harder to create cool air, and excessive cooling can cause a buildup of ice. Some air conditioners leak refrigerant slowly over time, and only a certified HVAC technician is qualified to fix this problem for you.
Low Outside Temperature
The final cause may simply be that the outside temperature is already near or below freezing levels. To prevent an ice buildup caused by freezing external temperatures, avoid engaging the air conditioner unit in cold temperatures.
DUCTLESS SYSTEM MAINTENANCE FROM THE HEAT PUMP STORE
Frozen mini splits can put a real damper on your day, so it’s best to avoid the problem altogether. You can prevent these issues entirely by scheduling regular maintenance for your ductless system. Experts from The Heat Pump Store offer services year-round to keep your system in top order. Contact our Salem, Portland, or Eugene locations today!
Get Your Ductless Cooling System Checked ASAP
Contact Us Today!